9 Dec Part AC metal-enclosed switchgear and controlgear for rated to IEC – the new standard for medium-voltage switchgear. All new medium-voltage switchgear assemblies installed after February 2, must fulfill the new standard IEC/EN 13 Sep IS/IEC High-Voltage Switchgear and Controlgear, Part AC Metal -Enclosed Switchgear and Controlgear for Rated Voltages.
|Published (Last):||10 October 2018|
|PDF File Size:||11.66 Mb|
|ePub File Size:||15.20 Mb|
|Price:||Free* [*Free Regsitration Required]|
Manufacturers and operators can select the criteria which are relevant to them from the following six criteria and have them tested.
IEC – HV Switchgear And Controlgear
For this reason, the test duties Ts and Ta from the IEC standard are stipulated for the test of the circuitbreaker inside the switchgear iec 62271 part 200. The vacuum arc-quenching principle is technologically so superior to other arc-quenching principles that the circuit-breaker can be fixed-mounted again.
Four key features are of special iec 62271 part 200 with the new IEC standard: The International Electrotechnical Commission IEC has taken up the task of developing the required specifications, their worldwide standardization and further development.
Facebook Linkedin Google Plus Twitter. Pressure and strength tests to verify the gas tightness and pressure resistance for gas-fi lled switchgear. Division of iec 62271 part 200 switchgear panel into four pwrt busbar compartment, switching-device compartment, connection compartment and low-voltage compartment ; partitions between the compartments made of sheet steel, front plate made of sheet steel or insulating material.
At the same time the old IEC standard was withdrawn without any transition period. Peak and short-time iec 62271 part 200 current tests to verify the dynamic and thermal current carrying capacity of the main and earth circuits; the tests are performed with rated peak short-circuit current or rated short-circuit making current or rated shorttime current or iec 62271 part 200 short-circuit breaking current.
AC metal-enclosed switchgear and controlgear for rated voltages above 1 kV and up to and including 52 kV. IEC — for four decades this kec was the decisive factor for the type testing of metal-enclosed switchgear. Mechanical function test to verify the mechanical functions and interlocks.
Premium Membership Premium membership gives you an access to specialized technical articles and extra premium content electrical guides and software. The passing of the following tests was obligatory in order to identify switchgear as type-tested: Switchgears are important nodal points in modern power distribution. However, both technologies — the vacuum lart principle and gas insulation — were not adequately taken into account in the existing standard.
Division of the switchgear panel same as for metal-clad switchgear, but iec 62271 part 200 the partitions between the individual compartments made of insulating material.
IEC | IEC Webstore
Therefore, at the end of the nineties, the responsible IEC committees decided on the reformulation of the switchgear standard, which finally came into effect as IEC in November According to IECtwo disruptive discharges were permitted in a series of 15 voltage impulses for the test with rated lightning impulse withstand voltage. Therefore, with switchgear in metalclad or compartmented design, the busbar in the busbar compartment and the incoming cable in the connection compartment could remain in operation.
Degree of protection tests to verify the protection against electric shock and foreign objects. Instead, it is now mandatory to carry out the test in the corresponding switchgear panel. Hi, For Auto Reclosures which we plan iec 62271 part 200 install for a 50 Iec 62271 part 200 system is it ok to accept the type test reports done in a 60 Hz laboratory???
Are there any published industry codes or standards that cover the inventory tracking, decommissioning, storage, chain of custody, disassembly, and disposal of the waste materials, etc. Professional in AutoCAD programming. The classification cannot be transferred to a combination with another switchgear type as each switchgear iec 62271 part 200 differently pxrt the case of an internal arc pressure relief equipment with different cross-sections and pickup pressures, different arcing conditions because of different conductor geometries.
Correspondingly important is their reliable functioning, a clearly defined switching behavior according to specified parameters as well as the protection of iec 62271 part 200 and protection against operational interruptions when an overload occurs. For Auto Reclosures which we plan to install for a 50 Hz system is it ok to accept the type test reports done in a 60 Hz laboratory??? Leave a Comment Click here to iec 62271 part 200 reply. The energy flow direction of the arc supply, the maximum number of permissible panels with the test in the end panel and the dependency of the ceiling height on the respective panel height have been redefined.
All other types of construction that do not meet the above features of the metal-clad or compartmented designs. For the internal arc classifi cation of substations with and without control aisle, iec 62271 part 200 testing of the substation with installed switchgear is mandatory in the new IEC standard.
In this context, access iec 62271 part 200 the then jec minimum-oil-content circuit-breakers for maintenance work without longer operational interruptions was of prime importance because of the limited number of operating cycles. The assignment is no longer according to the constructional description metalclad, iec 62271 part 200 or cubicle-type designbut according to operator-related criteria.
There is also the possibility of voluntarily certifying switchgear for resistance to internal arc faults and for personal protection.
Fit for IEC 62271-200?
According to the new standard, iec 62271 part 200 series must be extended by another fi ve voltage impulses if a disruptive discharge has occurred during the fi rst 15 impulses.
The switching capacity may get a negative infl uence from the different arrangement of the switchgear with contact arms, moving contacts, conductor bars, etc. Although the old IEC iec 62271 part 200 was very helpful, in time it was superseded by the technological progress.
Significantly stricter changes have also been implemented here. The classification of the substation is only valid in combination with the switchgear used for the test. Above all, the appearance of maintenance- free vacuum circuit-breakers, with operating cycles far exceeding the normal number, made frequent access to this circuit-breaker no longer of iec 62271 part 200 importance. In contrast to the previous standard, the switching capacity test of both switching devices is no longer carried out as a pure device test.
In addition, the five following new criteria must always be completely fulfilled no exceptions are permitted:.